AES Operates WORLDWIDE, on call 24 hours a day. Call us at 877-816-9081 OR Email
The Efficiency Experts
American Efficiency Services
Choose AES For Your Condenser Inspection & Tube Cleaning Needs!
We Are Available For You 24 Hours A Day, Every Day.
Electrical Generator Hydrogen System inspections can be conducted with the unit on or off line.
How Long Does The Inspection Take?
American Efficiency Services (AES) technique and experience can identify the sources of leakage within the hydrogen system, on average, within one 8 – 12 hour shift.
Why Do We Use Helium?
To date, identifying electrical generator hydrogen system leaks utilizing helium as a tracer gas, coupled with inspection experience, has proven to be the most cost effective method. One or two 219 - 291 cubic foot bottles of helium are introduced to the hydrogen system and the pressure is then increased to the generators operating pressure using additional hydrogen or dry air.
Once there is helium in the system, an AES inspector will inspect the flanges, drains, welds, and vents of the generator with a vacuum probe. If the vacuum probe enters an enriched area of helium created from a leak, an indication will be recorded on the helium mass spectrometer that is used for sampling. Any helium above background will provide an indication that will be isolated to the specific component leaking.
Most leaks can be repaired immediately while the inspection crew remains on-site to insure the repairs have actually reduced the leakage. In some instances, the system must be relieved of the pressure so repairs can be made. In these situations, the inspection crew can remain on-site during the de-pressurization, repair, and re-pressurization of the machine to confirm repairs. In lengthy repair evolutions, the crew can also be released and then re-assigned after the repairs to insure the systems integrity was achieved.
At the conclusion of the inspection, all results, retest results, and repair recommendations will be discussed with plant personnel, leaks photographed, leaks tagged, and a draft report filed.
Electrical Generator Hydrogen System Inspections
CALL US TODAY!